SE—Structures and Environment: Biofiltration of Odour and Ammonia from a Pig Unit—Biofiltration of Odour and Ammonia from a Pig Unit—a pilot-scale Study
Files in This Item:
|Biofiltration_of_Odour_and_Ammonia_from_a_Pig_Unit_Pilot_Scale_Study.pdf||1.09 MB||Adobe PDF||Download|
|Title:||SE—Structures and Environment: Biofiltration of Odour and Ammonia from a Pig Unit—Biofiltration of Odour and Ammonia from a Pig Unit—a pilot-scale Study||Authors:||Sheridan, B. A.
Curran, Thomas P.
Dodd, V. A.
|Permanent link:||http://hdl.handle.net/10197/4332||Date:||Aug-2000||Online since:||2013-05-22T11:00:50Z||Abstract:||A pilot-scale biofiltration unit was constructed at a pig finishing building on the University College Dublin research farm. The biofiltration system was investigated over three trial periods. Exhaust air from a single pen was extracted by a variable speed centrifugal fan and passed through a humidifier and biofilter. A 0·5 m depth of woodchips of over 20 mm screen size was used as the biofilter medium. The moisture content of the medium was maintained at 64±4% (wet weight basis) for trial one and 69±4% (wet weight basis) for trials two and three using a load cell method. The volumetric loading rate varied from 769 to 1898 m3 [air] m−3 [medium] h−1 during the three trial periods. Odour and ammonia removal efficiencies ranged from 77 to 95% and 54 to 93%, respectively. The pH of the biofilter leachate remained between 6 and 8 throughout the experimental periods. The pressure drop across the biofilter ranged from 14 to 64 Pa. It is concluded that a wood chip media particle size >20 mm is suitable for use in biofiltration systems on intensive pig production facilities. This will minimize the pressure drop on the system fans to reduce overall operation costs. It is recommended that a filter bed moisture content (wet weight basis) of greater than 63% be used to maintain overall efficiency. An efficient air moisturizing system (humidification and bed sprinkling) along with a properly designed air distribution system must be incorporated in the overall design when operating at such high volumetric loading rates.||Type of material:||Journal Article||Publisher:||Elsevier||Journal:||Biosystems Engineering||Volume:||82||Issue:||4||Start page:||441||End page:||453||Copyright (published version):||2002 Silsoe Research Institute. Published by Elsevier Ltd.||Keywords:||Biofiltration system; Odour reduction; Air moisturizing system; Ammonia removal||DOI:||10.1006/bioe.2002.0083||Language:||en||Status of Item:||Peer reviewed|
|Appears in Collections:||Biosystems and Food Engineering Research Collection|
Show full item record
This item is available under the Attribution-NonCommercial-NoDerivs 3.0 Ireland. No item may be reproduced for commercial purposes. For other possible restrictions on use please refer to the publisher's URL where this is made available, or to notes contained in the item itself. Other terms may apply.